Search waterheatertimer.org / all results
|Water heater sounds like it's running water.|
What is this? Should I be concerned? Nobody I talk with seems to know the answers.
Second email from Lavern: Hello Gene,
You are my hero!! I had called the water heater manufacturer, looked at several websites, and you were the only one who had the answer.
I was able to track down a small leak in the guest bathroom toilet, called a plumber, and it was fixed. The plumber was a very kind neighbor who didn't even charge me!! Now I hear the noise in the water heater tank only when I use water.
I am a 76 year old widow, and you saved me a lot of worry and money. Thank you so much!!
|My answers to emails become next topic for new webpage:
Email from Lavern arrived. She said:
My brand-new electric water heater periodically sounds like water running inside. When I shut off the valve at the top of the tank, the sound stops.
When you hear water running, it might be a water leak somewhere....
There are informal ways to check:
-Turn off all taps for 2-3 hours, and check water meter reading before and after. If homes is on water well, check pressure gauge before and after.
-Hot-cold pipes are attached to top of heater... when hot is running, the hot pipe feels warm to touch because the hot water is flowing through the pipe ... use hand to gauge temperature.
-Turn off all taps and put ear against hot pipe. If you hear sound of running water, there is probably a leak somewhere.
A continual leak will drain the hot out of tank, and evidence is hot water shortage.
-If your water pipes are under a slab, they can break and leak and you can see it, but you can hear it at the tank.
-If your water pipes are under a trailer or in a crawlspace, the leak might not be noticable.
-There is a TP valve located on side of heater, with an overflow tube... if this tube just goes to bottom of heater, you can visually see if it's leaking ... but if the overflow tube goes through the wall somewhere, the TP valve might be leaking ... put hand on pipe to see if it feels warm.
-The TP valve will leak water out of tank if the TP is faulty or water inside tank is overheating... both unlikely with new heater, but common with older heaters.
-Cause can be a cold water leak, where the sound is broadcasting through the pipes and you can hear it at the heater./... the culprit can be broken pipe under slab, or something simple like a toilet overflow running... for example do your toilets have a 'phantom flush' where you can occasionally hear them refilling..?
-Toilets are not connected to Hot pipe... but one unusual case, the homeowner finally discovered his hot water shortage was caused by a 'contractor' connecting toilet to hot pipe instead of cold ... but not before he purchased and installed a new water heater.
Buy from my associate links:
50 gallon Gas water heaters at Amazon
40 gallon gas water heaters at Amazon
50 gallon Electric water heaters at Amazon
40 gallon electric water heaters at Amazon
Hybrid / heat pump/ water heaters at Amazon
How to install gas water heater
How to install electric water heater
Troubleshoot gas water heater
Troubleshoot electric water heater
Point of use water heaters
Tools and home improvement
Home and garden
Black and Decker
Irwin Hand tools
Klein hand tools
Fluke electrical testing
Dremel hobby tools
Campbell Hausfeld air powered
Saws and saw blades
Compare box timers
Control water heater w/ Z-wave
Intermatic control centers: and parts
Digital control centers and parts
Tork control centers and parts
All control centers and parts
Off delay timers
On delay timers
Twin & one-shot
|Enter Amazon from
My response might end up in spam folder, check email folders
Follow latest idea on twitter